Extension of the characteristic equation to absorption chillers with adiabatic absorber=Extension d'une équation caractéristique aux refroidisseurs à absorption munis d'absorbeurs adiabatiques
electronic international standard serial number (EISSN)
Various researchers have developed models of conventional H2O-LiBr absorption machines with the aim of predicting their performance. In this paper, the methodology of characteristic equations developed by Hellmann et al. (1998) is applied. This model is able to represent the capacity of single effect absorption chillers and heat pumps by means of simple algebraic equations. An extended characteristic equation based on a characteristic temperature difference has been obtained, considering the facility features. As a result, it is concluded that for adiabatic absorbers a subcooling temperature must be specified. The effect of evaporator overflow has been characterized. Its influence on cooling capacity has been included in the extended characteristic equation. Taking into account the particular design and operation features, a good agreement between experimental performance data and those obtained through the extended characteristic equation has been achieved at off-design operation. This allows its use for simulation and control purposes.
absorption ; lithium bromide ; temperature difference ; chilled water ; air conditioning